Fire Door Seals or Fire and Smoke Seals
Intumescent fire door seals should be fitted to the stiles and head of a fire-resisting doorset. These seals are fitted into grooves cut into the door or the frame, or alternatively, can be surface mounted. As soon as the temperature in the vicinity of the strips exceeds 200°C, usually about 10-15 minutes after the start of a fire, the seal swells and seals the gaps between door and frame.
As smoke spread is an even greater threat to life and property than flames, particularly in the early stages of a fire, fire doors might also have to be fitted with a ‘cold smoke’ seal to prevent the ingress of smoke around the door edges (such fire doors would be specified as FDs fire doors). Exceptions apply where the leakage of smoke is essential for detecting a fire early. Combined smoke and intumescent seals are available.
Not all intumescent materials act in the same way. Low pressure seals expand in all directions but provide little help to the door in resisting distortion under fire. Some high pressure seals exert pressure mainly in one direction and provide some resistance to distortion of the door leaf under fire. A further type of intumescent material, available in different grades, acts in all directions and generates some pressure. Fire door seals activate at temperatures that are above human survival levels. The following is information on the type or size of intumescent fire door seal that should be used.
Most modern fire door seals combine the intumescent and cold smoke elements in one seal.